PP-coated system pipe made of non-alloyed steel 1.0308 (E235)
Galvanised (blue chromated) on the outside.
Covered on the outside with a polypropylene (PP) plastic coating in white (RAL 9001).
Suitable for heating, solar and cooling systems.
System pipe made of non-alloy steel 1.0215 (E220)
Hot dip galvanised on the outside and inside.
Suitable for sprinkler and compressed air systems.
Manufacturer, pipe dimension, batch, red dot on press end, symbol »Not approved for potable water installations«, red line on the pipes, red pipe plug, white pipe plug (hot dip galvanised), detachable orange label as press indicator from d64.0
Press connector with SC‑Contur
Inadvertently unpressed connections are noticed immediately during a leakage test.
Viega guarantees the detection of unpressed connections in the following pressure ranges:
min. water pressure: 0.1 MPa / 1 bar / 14.5 PSI
max. water pressure: 0.65 MPa / 6.5 bar / 94.3 PSI
min. air pressure: 22 hPa / 22 mbar / 0.3 PSI
max. air pressure: 0.3 MPa / 3 bar / 43.5 PSI
EPDM (ethylene propylene diene rubber), black, pre-assembled
d12–108.0, size availability in accordance with the national regulations
The functional safety of Viega press connector systems depends primarily on the faultless condition of the press tools used. For the manufacture of press connections, Viega recommends the use of Viega press tools. Viega press tools have to be regularly maintained by authorised service partners.
Areas of application
Closed cooling and heating systems
Industrial and plant engineering
Sprinkler systems (hot dip galvanised pipe)
Compressed air systems (hot dip galvanised pipe)
Solar installations with flat collectors
Solar installations with vacuum collectors (only with FKM sealing element)
Use of the system for areas of application and media other than those described must be agreed in consultation with Viega! Detailed information about applications, restrictions and national standards and directives can be found in the product information, either printed or on the Viega website.
Note – Standards and approvals
Press connector system with press connectors and pipes in accordance with DIN EN 10305‑3.
For use in heating systems, observe VDI Regulation 2035 and DIN EN 12828.
Operating conditions with EPDM sealing element
operating temperature max. 110 °C / 230 °F
operating pressure max. 1.6 MPa (PN16) / 16 bar / 232 PSI
Material press connector
Note – Storage and transport
To ensure the impeccable quality of Prestabo pipes, observe the following points during transport and storage:
Packing and protective foil (on with PP coated pipes) should not be removed until immediately before use.
The pipe ends must be closed with protective caps when delivered.
Do not store the pipes directly on the bare floor.
Do not stick any protective foils or plastics to the pipe surfaces.
When loading and unloading, do not pull the pipes over the truck sill.
Note – Protection against external corrosion
Prestabo pipes and press connectors are protected by external galvanisation.
In case of contact with dampness (condensation, precipitation during the construction phase, plaster and splash water etc.) or corrosive building materials (surfacer, levelling screed etc.), however this layer of zinc cannot provide permanent protection against external corrosion. the following protective measures are recommended:
Use of closed-cell insulating tubes with professional sealing of all abutting and cut edges using a suitable filler.
Damp-proofing of the laid pipe through separating foil in the floor construction.
Installing pipes outside areas at risk of moisture.
Visible radiator connections rising from the floors should be avoided if floors will be frequently cleaned with water and/or cleaning agents/disinfectants, for example in retirement homes and care facilities, as well as hospitals. Wall connections make cleaning easier and also exclude any additional risk of corrosion.
If the radiator connections do come from the floor, professional corrosion protection and professional sealing of the joints are ensured. If not, there is a possibility that the cleaning water will penetrate, which will moisten the insulation and present the risk of corrosion.
If the measures in the examples above fail to provide permanent protection against dampness or the areas of use have to meet special requirements, e.g. in cooling circuits, complete external corrosion protection, which reliably prevents influences that lead to corrosion, must be applied.
Pressure gradient calculator
Web application for quick and simple calculation of pipeline dimensions for potable water, heating and gas supply lines with associated pressure loss tables across the entire system.
Subject to change without prior notice!
Latest Z- and installation dimensions as well as further technical information can be found on the Viega website and have to be checked before purchase, planning, construction work and use. Our products are continuously optimised.
This product description contains important information on choice of product and system, mounting, commissioning as well as intended use and, if required, on maintenance measures. This information on products, their features and application techniques is based on currently valid standards in Europe (e.g. EN) and/or in Germany (e.g. DIN/DVGW). Some passages in the text may refer to technical regulations in Europe/Germany. These should be considered as recommendations for other countries where no corresponding national requirements exist. The relevant national laws, standards, regulations, directives and other technical provisions take priority over the German/European directives specified in this product description: The information herein is not binding for other countries and regions and should be understood as recommendation.