Press connector system with press connectors made of copper and gunmetal tested in acc. with DVGW worksheet W 534 with DVGW test seal and pipes made of copper in acc. with EN 1057 in acc. with DVGW worksheet GW 392.
Suitable for potable water installations in acc. with DIN 1988.
For dimensionally stable concealed and pre-wall installations of manifold and riser pipes in Viega component assembly.
All sizes with SC‑Contur – connections, which remain unpressed become visible when the system is filled. The SC‑Contur is certified and fulfils the requirements of DVGW worksheet W 534, Point 12.14, Connectors with forced leakage.
During leakage tests with water, Viega guarantees the identification of unpressed connections in the pressure range 0.1 MPa–0.65 MPa, in the case of a dry leakage test with compressed air or noble gases from 22 hPa–0.3 MPa.