Flow-optimised press connector system with press connectors made of stainless steel 1.4401 and pipes from stainless steel 1.4401 and 1.4521. Free of paint-wetting impairment substances (PWIS-free) such as silicone, grease or oil. Especially suitable for the use of piping installations in paint shops. Press connectors for protecting the sealing element equipped with cylindrical pipe guide. Press connectors from d64.0 with stainless steel cutting ring to ensure the mechanical strength of the connection. For protection pipes are equipped with pipe plugs. The pressing force is located before and behind the sealing element seat. Suitable for concealed and pre-wall installations of riser pipes and floor installations.
Marking Manufacturer, pipe dimension, batch, blue dot on the press end, yellow pipe plug for 1.4401, green pipe plug for 1.4521, detachable orange label as press indicator from d64.0
Press connector with SC‑Contur Inadvertently unpressed connections become visibly leaky when the system is filled. Viega guarantees the detection of unpressed connections in the following pressure ranges: min. water pressure: 0.1 MPa / 1 bar / 14.5 PSI max. water pressure: 0.65 MPa / 6.5 bar / 94.3 PSI min. air pressure: 22 hPa / 22 mbar / 0.3 PSI max. air pressure: 0.3 MPa / 3 bar / 43.5 PSI
Sealing elements EPDM (ethylene propylene diene rubber), black, pre-assembled
Tools The functional safety of Viega press connector systems depends primarily on the faultless condition of the press tools used. For the manufacture of press connections, Viega recommends the use of Viega press tools. Viega press tools have to be regularly maintained by authorised service partners.
Areas of application Potable water Rainwater Compressed air systems Agriculture Industrial applications
Note The press connector system Sanpress Inox LF is suitable for the creation of potable water installations according to DIN 1988‑200 and EN 806‑2 in consideration of the selection of material in accordance with DIN EN 12502‑1 and according to the evaluation basis for metallic materials in contact with potable water of the Umweltbundesamt (UBA) (Federal Environment Agency). When used for other areas of use and when in doubt about the right selection of material, please contact Viega. The system components should be protected against high concentrations of chloride generated by both the medium and by external factors. Detailed information about applications, restrictions and national standards and directives can be found in the product information, either printed or on the Viega website.
Note – Standards and approvals Pipe approval for 1.4521 (d12–108.0) according to DW-7301BS0375. Pipe approval for 1.4401 (d12–108.0) according to DV -7301BS0411. System approval for 1.4401 (d15–108.0) in accordance with DW-8501BL0551. System approval for 1.4521 (d15–108.0) in accordance with DW-8501BS0376.
Special applications Shipbuilding Fire extinguishing systems
Operating conditions for potable water installations operating temperature max. 85 °C / 185 °F operating pressure max. 1.6 MPa / 16 bar / 232 PSI Irrelevant of the flow direction, mixed installations are permitted.
Material press connector Stainless steel 1.4401
Pressure gradient calculator Web application for quick and simple calculation of piping dimensions for potable water, heating and gas supply lines with associated pressure loss tables across the entire system.
Subject to change without prior notice! Latest Z- and installation dimensions as well as further technical information can be found on the Viega website and have to be checked before purchase, planning, construction work and use. Our products are continuously optimised.
This product description contains important information on choice of product and system, mounting, commissioning as well as intended use and, if required, on maintenance measures. This information on products, their features and application techniques is based on currently valid standards in Europe (e.g. EN) and/or in Germany (e.g. DIN/DVGW). Some passages in the text may refer to technical regulations in Europe/Germany. These should be considered as recommendations for other countries where no corresponding national requirements exist. The relevant national laws, standards, regulations, directives and other technical provisions take priority over the German/European directives specified in this product description: The information herein is not binding for other countries and regions and should be understood as recommendation.