Press connector with SC‑Contur
Inadvertently unpressed connections become visibly leaky when the system is filled.
Viega guarantees the detection of unpressed connections in the following pressure ranges:
min. water pressure: 0.1 MPa / 1 bar / 14.5 PSI
max. water pressure: 0.65 MPa / 6.5 bar / 94.3 PSI
min. air pressure: 22 hPa / 22 mbar / 0.3 PSI
max. air pressure: 0.3 MPa / 3 bar / 43.5 PSI
EPDM (ethylene propylene diene rubber), black, pre-assembled
The functional safety of Viega press connector systems depends primarily on the faultless condition of the press tools used. For the manufacture of press connections, Viega recommends the use of Viega press tools. Viega press tools have to be regularly maintained by authorised service partners.
Areas of application
Compressed air systems
The press connector system Sanpress LF is suitable for the creation of potable water installations according to DIN 1988‑200 and EN 806‑2 in consideration of the selection of material in accordance with DIN EN 12502‑1 and DIN 50930‑6. When used for other areas of use and when in doubt about the right selection of material, please contact Viega. The system components should be protected against high concentrations of chloride generated by both the medium and by external factors. Detailed information about applications, restrictions and national standards and directives can be found in the product information, either printed or on the Viega website.
Note – Standards and approvals
Press connector system with press connectors and pipes in accordance with DIN EN 10088, DIN EN 10312, DVGW Worksheet GW 541 and W 534.
Pipe approval for 1.4521 (d12–108.0) according to DW-7301BS0375.
Pipe approval for 1.4401 (d12–108.0) according to DV -7301BS0411.
System approval for 1.4401 (d12–108.0) in accordance DW-8501AP3032.
System approval for 1.4521 (d12–108.0) in accordance with DW-8501BS0377.
Operating conditions for potable water installations
operating temperature max. 85 °C / 185 °F
operating pressure max. 1.6 MPa / 16 bar / 232 PSI
Irrelevant of the flow direction, mixed installations are permitted.
Material press connector
Copper: 99.9 % Cu-DHP
silicon bronze: CC246E / CuSi4Zn9MnP
Pressure gradient calculator
Web application for quick and simple calculation of pipeline dimensions for potable water, heating and gas supply lines with associated pressure loss tables across the entire system.
Subject to change without prior notice!
Latest Z- and installation dimensions as well as further technical information can be found on the Viega website and have to be checked before purchase, planning, construction work and use. Our products are continuously optimised.
This product description contains important information on choice of product and system, mounting, commissioning as well as intended use and, if required, on maintenance measures. This information on products, their features and application techniques is based on currently valid standards in Europe (e.g. EN) and/or in Germany (e.g. DIN/DVGW). Some passages in the text may refer to technical regulations in Europe/Germany. These should be considered as recommendations for other countries where no corresponding national requirements exist. The relevant national laws, standards, regulations, directives and other technical provisions take priority over the German/European directives specified in this product description: The information herein is not binding for other countries and regions and should be understood as recommendation.